Water Treatment Equipment
High frequency electronic water treatment instrument
1. Product Introduction
Electronic water treatment device is to use high frequency electromagnetic field to electromagnetically process the water flowing through the main pipe of the water treatment device. After the water passes through the electronic water treatment device, the degree of polymerization is reduced, the structure is deformed, and a series of small elastic changes in physical and chemical properties are generated. The dipole moment increases and the polarity increases, thus increasing the hydration capacity and scale dissolving capacity of the water. To the role of anti-scaling and descaling; under the action of electromagnetic fields, the micro current generated by the dipole destroys the enzyme system on which the cells depend, thereby playing the role of sterilization and algae elimination.
The device has an automatic operation function, which can effectively process different water quality through the specified parameters of the specific output. Its intelligent and composite electric field technology ensure the best treatment effect.
2. Product working principle
● Descaling and anti-scaling
Based on the electromagnetic principle of the Belgian scientist Dr. Lorenz, the Nobel Prize winner, combined with the research and experience of many cutting-edge technologies, a new generation of multi-functional high-frequency electronic water treatment device was successfully developed. Using modern electronic technology and molecular surface energy rearrangement technology, after the water body absorbs high-frequency electromagnetic energy, its physical structure is changed without changing the original composition, and the original associated chain-shaped macromolecule breaks into a single water molecule The positive and negative ions of dissolved salts in the water are surrounded by a single water molecule, the movement speed is reduced, the number of effective collisions is reduced, and the electrostatic attraction is reduced, so that the calcium and magnesium ions in the water cannot combine with the carbonate to form calcium carbonate and magnesium carbonate, thereby achieving scale prevention effect. At the same time, because the water body absorbs a large number of excited electrons, the dipole moment of the water is increased, and the affinity of the positive and negative ions of the salt is increased, so that the original scale on the wall of the tube is gradually loosened and even shedding, achieving an effective descaling effect .
● Sterilization and algae elimination
High-frequency electromagnetic waves produce turbulence in the water, destroying the ion channels of the cell membrane, changing the internal control current that the cell adapts to and the environmental conditions required for survival, causing it to lose its ability to survive and die. At the same time, the activated water molecules can surround and block the dissolved oxygen in the water, cutting off the source of oxygen needed by microorganisms for life reaction, thereby achieving a good sterilization and algae elimination effect and preventing the generation of biological sludge.
● Anticorrosion and rust removal
When the water body receives the action of high-frequency electromagnetic energy, a single water molecule contains the oxygen molecules dissolved in the water, so that the dissolved oxygen becomes inert oxygen, cutting off the source of oxygen required for metal corrosion. At the same time, the “skin effect” generated by the electromagnetic field of the overhanging composite modulation frequency excited by the high-frequency electromagnetic waves accumulates excessive negative charges on the wall of the tube, and excessive positive charges accumulate inside the water. The excessive positive charges in the water strongly repel the band The positively charged Fe + prevents Fe from losing electrons to become Fe +, and prevents Fe from separating from the metal wall into the water (the yellow rust water produced in the system is the color of Fe + in the water). At the same time, the excess negative electrons on the wall of the tube also continue to attract positively charged Fe +, which prevents Fe + from dissolving into the water, so that the original Fe2O3 (red rust) on the wall of the tube can be reduced to a black rust coating with strong corrosion resistance. Fe3O4.
3. Product Features
● Does not change the chemical properties of water, without any side effects on the human body.
● The descaling effect is obvious. The equipment is installed in the water circulation system. For the original scale thickness below 2mm, it can be gradually loosened and loosened in about 30 days. The treated scale is granular and can be discharged with the sewage pipeline without blocking the pipeline system,. After the old scale has fallen off, no new scale will be produced within a certain range.
● The equipment is small in size, easy to install, and can be used unattended for a long time.
● After the water flows through the device, it can turn the water into magnetized water, and it can inhibit and kill bacteria in the water.
● Does not corrode equipment, can extend the service life of servo equipment.
4. Product model description
The equipment is divided according to the inlet and outlet diameters. The conventional products are DN50, DN65, DN80, DN100, DN125, DN150, DN200, DN250, DN300, DN350, DN400, DN450, DN500, DN600, etc. 14 specifications, according to the pressure can be divided into pressure 1.0 MPa, 1.6MPa.
5. Product Technical Data Sheet
6. Technical performance parameters
● Working pressure: ≤1.6MPa
● Working temperature: ≤95 ℃
● Effective anti-corrosion: ≥98%
● Effective anti-rust: ≥98%
● Anti-scaling and descaling rate: ≥98%
● Resistance loss: ≤1.5m water column
● Electric power: 10 ～ 400W
7. Technical considerations
1. This machine uses 220v AC power, and the voltage and frequency fluctuations meet the requirements of the input power item in the operating parameter table. (Warning: It is forbidden to turn on the device for a long time without water)
2. The equipment specifications are national standard flange connection.
3. For the electronic water treatment device: Connect the circuit with the random power cord, turn on the electronic water processor power switch, the power indicator and the electrode display light indicate that the electronic water treatment device is working normally, the electronic water treatment device of this specification is automatically operated There is no manual adjustment function. The operating parameters of the product have been set before leaving the factory. The user cannot debug or disassemble the electric controller without consent.
4. The circulating water system of the electronic water treatment device must have a sewage outlet for regular sewage discharge, and the concentration ratio of the circulating water should not exceed 2.5 (relative to the original water).
8. Installation and commissioning
1. Power supply configuration: Please select the power socket, wire or wiring board according to the voltage and power indicated on the nameplate.
2. Installation principles and precautions:
1) The electronic water treatment device should be connected in series in the pipeline, the specific installation is shown in the figure, and accessories can be added according to the installation requirements.
2) The electronic water treatment device should be installed as far as possible before the equipment to be protected, as close as possible to the import and export of water equipment. In the power system, the electronic water treatment device should be installed between the pump and the equipment, and should be as close as possible to the protected equipment. If the pressure between the pump and the device exceeds the limit pressure of the electronic water treatment device, the electronic water treatment device should be installed in front of the pump and as close as possible to the pump.
3) In the circulation system, the electronic water treatment device should be installed on the main circulation pipeline, and cannot be installed on the make-up water. The specific installation is shown in the figure. If the conditions restrict the installation, you can install it according to the picture.
4) There must be no water tank or storage tank between the electronic water treatment device and the water-using equipment.
5) A bypass line should be installed at the inlet and outlet of the electronic water treatment device, so that the water treatment device can be repaired without stopping the machine. The specific installation is shown in the figure.
6) The new equipment can be directly installed with an electronic water treatment device. For water equipment with serious scaling (scale thickness> 3mm), the scale must be removed before installing the electronic water treatment device to prevent the old scale from falling off and blocking the pipeline.
7) During the installation and transportation, do not force the electric controller.
8) Reasonably choose the installation environment, pay attention to waterproof, rain and moisture.
9) Above the electric controller or along the opening direction of the electric controller cover, a clear space of not less than 600mm should be reserved for maintenance.
3. Installation location
1) Non-circulating hot water system
◆ For non-circulation hot water system, it is recommended to install a check valve before the boiler inlet pipe to prevent steam or boiling water from entering the electronic water treatment device.
2) Circulating hot water system: The cold water and hot return water entering the water heater all need to go through the electronic water treatment instrument, and the specific installation is shown in the figure.
1. The green indicator light in this instrument is the power indicator, and the red indicator light is the work indicator. If during the initial installation or use, you find that all the indicators are off, please check whether the power supply has power, whether the power switch is turned on, whether the power socket is plugged in firmly, and whether the fuse in the power socket on the instrument is intact In the lower part of the power socket, you can use a flat-tip wire knife to open the fuse box cover along the slot. If there is no problem, please contact the manufacturer in time.
2. The electrical part has burnt smell and smoke generation should immediately cut off the power supply and notify the after-sales service.
3. There is a fuse in the power socket of the instrument. If the fuse is blown, please replace the fuse by yourself.
4. If you find that some of the indicators are off or other faults occur during work, please contact your home in time.
5. Never open the casing of the electric controller without authorization, otherwise the manufacturer will not be responsible for the product warranty.
ONLINE / MESSAGES
CopyRight © 2020 Youxin Group ICP: 鲁ICP备18012254号-1 Powered by www.300.cn