Water Supply Equipment
Constant pressure water supply device
1. Product Introduction
The bladder floor expansion water tank is also called constant pressure water replenishment device. It is a constant pressure water replenishment device. It is widely used in air conditioning, heating systems, water supply pipe network systems, etc. It can replace the traditional expansion water tank water tank and can reduce the number of pump start It can absorb part of the water expansion of the system, and it is easy to realize automatic water replenishment, automatic exhaust, automatic pressure relief and automatic overpressure protection.
2. Product working principle
Constant pressure water replenishment device uses gas expandability to work. It is mainly composed of bladder type constant pressure tank, water pump, pressure switch, control box, safety valve, base, and connecting pipeline. When the volume of water increases when the temperature in the system increases, the system pressure increases. At this time, some water will enter the capsule of the bladder constant pressure tank. The expansion of the capsule will compress the gas in the tank until the pressure of the system and the tank Until the pressure inside reaches equilibrium. When the volume of water in the system decreases and the system pressure decreases, the gas in the tank expands to push the water in the bladder back to the system. If these amounts of replenishment still cannot meet the amount of water required by the system, the pump starts replenishment. The starting and stopping actions of the water pump are controlled by the electrical contact pressure gauge of the system and the control box. The electrical contacts have two set pressure points, one is the pump start pressure P1, and the other is the pump stop pressure P2, P1 and P2 are the system's lowest fixed pressure point and the highest working pressure, respectively. When the system pressure does not reach P1 after replenishing water through the bladder constant pressure tank, the control box controls the water pump to turn on to replenish water to the system. When the system pressure and the pressure in the tank are greater than P2, the pump stops.
3. Main features of the product
1. Nitrogen gas can be used for a long time.
2. The tank is a closed device, and the gas and water are not in contact, which can ensure that the water quality is not polluted by the outside world.
3. It occupies less area, saves investment, is quick to install, and easy to operate and maintain.
4. Eliminate the high water tank in the building and save structural investment.
5. The water tank acts as a buffer to eliminate the impact of water hammer on the pipe network.
6. Automatic control and reliable operation.
7. The expansion and contraction of the water body of the regulating system due to temperature fluctuations-expansion and contraction.
8. Make the pressure of a certain point of the system constant-constant pressure.
9. When the system leaks, add water to the system-make up water.
4. Notes on installation of constant pressure water supply device
1. The distance between the equipment and the wall or other equipment should be no less than 0.7m.
2. The room with constant pressure water supply equipment should have excellent ventilation, and the indoor temperature should not be lower than 5 ℃ and not higher than 40 ℃. When the equipment is frozen in a dangerous outdoor environment, you should consider measures such as weather and frost protection.
3. After the hydraulic pressure strength test and the tightness test of the pneumatic tank are qualified, the debugging should be carried out according to the engineering design request. After the commissioning work is completed, ensure that the inflatable mouth does not leak.
4. The equipment is qualified for commissioning. After it is put into operation, it is not necessary to have someone on duty for constant pressure water replenishment. Note the installation of fixed pressure water replenishment device but regular inspections are required.
5. User Manual of Constant Pressure Water Supply Device
ONLINE / MESSAGES